The ejector/check valve assembly shall be of the chlorine water solution feed type and shall create the vacuum necessary to operate the system.
The ejector/check valve assembly shall be a spring-opposed, O-ring seal, diaphragm type. The ejector/check valve shall be suitable for a maximum capacity of 6000PPD/120 kg/h against a maximum backpressure of 75 psig. The springs shall be tantalum alloy.
The ejector shall have a 1-1/2 inch vacuum connection and 3” 150lb flanged water supply inlet and solution outlet.
The following ejector spare parts shall be provided:
1-One (1) set ejector diaphragms.
2-One (1) set ejector gaskets & O-Rings.
The ejector/check valve assembly shall be DE NORA WATER TECHNOLOGIES, INC. ADVANCE EJ6000C.